Arrived to multiple alert System was faulting on Low Superheat Tested system and adjusted OD unit configuration from 2 to 3 tons to accurately reflect size of outdoor unit. Tested system , maintained a SH of 8-12* and 15-17* in heating
DCM2; Heat; (3) F14141 and (2) F14201 replaced. Systems are fully functional. All components operating within manufacturers specifications. Gas pressures and temperature rises are within design parameters. Heat checklist attached.
DCM2 complete; AC; (1) F16201 and (1) F20201 replaced. Systems are fully functional. All components are operating within manufacturer specifications. Refrigerant pressures and temperatures are appropriate for indoor and outdoor conditions. AC checklist attached.
Heat maintenance on 2-systems in Conley