DCM2 service 1 of 2 Heat completed changed (2) 14x20x1 washed mini split filters, tested system operation’s everything is operating properly at this time attached is Heat maintenance checklist.
Picked up Portable
No a/c call, on arrival system was off turned on and checked operation found that the condenser fan was not running due to bad dual capacitor that was swollen, burnt and reading 0, also found that the hard start is weak reading 111 manufacturing specs should be between 135 - 162, with homeowners permission replaced the dual capacitor only checked operation 129/256, SH18, SC4 system is running at this time.
DCM1 service 2 of 2 AC completed changed (1) 16x25x1 filter, tested system operations everything is operating properly at this time attached is AC maintenance checklist.
DCMQ service 1 of 2 AC completed changed (1) 16x25x1 filter, tested system operations everything is operating properly at this time attached is AC maintenance checklist.
DCM2 service 1 of 2 AC completed changed (1) 16x20x1 filter, washed (1) mini split filter, tested system operation found mini split empty of all refrigerant, did complementary leak search and found leak at liquid line fitting, repairs and tightened connection to ensure no leak is present. Added (2) pounds of 410A to system unit now operating properly at this time. Main Goodman package unit is operating properly at this time, compressor capacitor is weak 40MFD reading 34.7. Unit is operating however as capacitor gets weaker the potential for part failure is increased. Ductwork in crawlspace needs attention, many connections are not sealed properly resulting in airflow to be released into crawlspace, there is a major break closer to the package unit, where ductwork enters crawlspace. Recommend sealing of all connections and re insulation of wet ductwork. Confirmed Thursday in the 1-2 arrival for comfort specialist to look over ductwork, crawlspace is on right side of home, contact landlo
Routine heat maintenance in Cartersville
Servicing gas furnace in Cartersville
Servicing a gas furnace in Cartersville