Professional, equipped with latest technology for diagnosis of systems so obviously up to date on training. Used foot-bootie so no mess left behind. Put all the settings back the way they were after performing his tests. Also just got a really good vibe from Rob, sounds silly but with me it's important to trust your gut . Last but not least a van load of salesman did NOT appear on my doorstep trying to sell me stuff like the last 2 different companies I've had experience with.
Excellent and efficient work by Cody to get my A/C up and running for the season. He did a thorough inspection and quick troubleshooting to solve a minor problem. Very glad I called Dobbs.
Dobbs Heating & Air is the best! Great people who are professional, on time and affordable.
Hands down the best experience I've had with an A/C company. Rob was on time, thorough, and so friendly. Every person I interacted with at Dobbs was friendly, professional, and the communication was flawless. Would absolutely recommend.
No a/c system has bee freezing up, on arrival turned on and found system to be low on charge, 33/167, SH54, talked to homeowner and he wanted to charge system up at this time, added 1lb of R22 to system new psi 64/205, SH18, system is running at this time but due to age and condition multiple part failure is possible at anytime, it is recommended to consider replacing and upgrading system due to age, condition, efficiency, amount of repairs, and the fact that R22 is phased out.
Arrived to System #5 and System #6 drain lines clogged. System share a communal drain. Drainage system had multiple clogs in both the communal lines and individual lines. Cleared all connecting drains. Checked water safeties, function as designed Water had escaped pan on System #6, auxiliary pan drain stub was loose. Tightened to ensure proper seal and to prevent drain pan leakage
Removed old electric meter monitor wire.
Upon arrival checked over system investigated water dripping from ceiling. Checked over package Unit on roof. Drain pan is leaking water into system and then further down into ceiling. Drain pan is metal and has significant amount of rust, erosion and oxidation which has caused water to leak. Preformed safety inspection on heat exchangers found multiple holes and cracks in heat exchangers. Heat exchangers must be sealed, during the heating season with a crack or hole there is a greater possibility of carbon monoxide leaking into space, system has 13 different holes, and cracks. Would strongly recommend to not run heat until Heat Exchangers are replaced or system is replaced. System is running on R22 refrigerant system holds 6 pounds 6 ounces, system is low on R22 roughly 1-2 pounds.R22 is no longer in production due to EPA regulations, supply of R22 is dwindling, there is dye present in system, this indicates there is a known leak inside. If drain metal drain pan is replaced all refrig
Picked up Portable
Dobbs Heating and Air is committed to providing top quality heating and air conditioning services, HVAC unit replacements, HVAC Repair, and new Heating and Air installations to the Atlanta Metro area every day. With high quality service & incomparable customer service, you can count on Dobbs to deliver on your heating and air conditioning needs. Call us at 770-445-8923 for the best Local HVAC Repair, Replacement, Installation, or Maintenance you could hope for!
The list of Metro Atlanta, West Georgia, and Northwest Georgia cities, towns, and communities that we offer service for is always expanding. Even if you don’t see your county, city, town, or community listed, please don’t hesitate to call Dobbs Heating and Air. One of the great advents of existing in a fresh, growing company is the potential to expand our service area horizon with the same kind of flexibility that we can continue to expand our services rendered. We have offered high quality service, and continue to offer service to most of the area in and around the Metro ATL area. The specific locations of our serviced areas for Local HVAC Repair include, but are not limited to the following:>
Are you anywhere in or around the Metro Atlanta area? Are you in the North or West Metro ATL, and looking for the services of a high-qualified, Local HVAC Repair Company? From Cherokee County to Carroll County, Dobbs Heating and Air is the fastest-growing Local HVAC Company. From Forsyth County to Fulton County, Dobbs HVAC is gaining a Metro-Wide reputation as a great local HVAC company that offers amazing customer care to each and every commercial or residential customer. Cobb County? Dekalb County? Haralson and Bartow Counties? From Paulding County to Polk County, everywhere in between, and everywhere beyond, Dobbs is steadily rising, one satisfied customer at a time, as the name to trust for Local HVAC Repair in Metro Atlanta, West Georgia, Northwest Georgia, and beyond. Call or Contact Us to schedule a FREE On-Site Assessment of your Heating and Air Needs, we can help with anything like:
Your Dobbs Local HVAC Repair Professional is ready, willing, and able to help with all your local HVAC Repair, Replacement, Installation, Maintenance, or Service needs. Schedule an appointment at your home or business!