Technician show up on time and was very professional.
Always happy with Dobbs service. Did a great job and explained everything along the way.
Keith is great!
Rep was friendly and efficient. As this is a service that we have done two times per year he asked me what I would like for the temperature settings in our Climate Controlled buildings. They are great for business.
DCM1 service 1 of 2 Heat Homeowner replaces filters, performed heating maintenance per checklist, system is running at this time.
DCM1 service 2 of 2 heat completed changed (1) 14x25x1 filter, filter was impacted recommend replacing every 3 months, tested operation everything is operating properly at this time, attached is Heat maintenance checklist.
DCM1 service 1 of 2 heat completed, was unable to change filter due to washing machine being in the way left (1) 16x20x1 to be changed. Tested system operation’s everything is operating properly at this time attached is Heat maintenance checklist.
DCM1 service 1 of 2 heat completed changed (1) 20x20x1 filter, tested system operation’s everything is operating properly at this time attached is Heat maintenance checklist.
DCM1 service 1 of 2 heat completed changed (1) 12x24x1 filter,tested operations, outdoor AC is not operating found capacitor is bad 45/5 MFD reading 0MFD, system will not operate in AC mode. In heat mode found unit has crack (compromised) heat exchanger on the face plate and has potential to leak carbon monoxide into home. Current carbon monoxide readings in home is 1PPM. . Blower wheel is dirty to the point which negatively affects airflow and efficiency, Unit is from 2001 and is beyond life expectancy due to age and conditions of furnace would recommend replacement. Called Charlie and left a voicemail, attached is Heat maintenance checklist.
DCM1 service 1 of 2 heat completed changed (1) 16x25x4 filter, tested system operation’s, adjusted fan speed on heat from low to medium to help keep furnace from running too hot. Everything is operating properly at this time attached is Heat maintenance checklist.
DCM1 service 1 of 2 Heat completed changed (1) 24x24x1 filter, tested system operation’s is operating properly at this time attached is heat Maintenance checklist.
DCM2: Service 2 of 2, AC, Changed (1) 16x25x1 (1) 16x25x4, Performed Cooling maintenance Per Checklist, Main Level system is low on charge 1 to 2lbs of R22 system is 15 years old and beyond life expectancy it is recommended to consider replacing and upgrading main level system, homeowner declined options at this timeSystems are running at this time.
DCM3: Service 2 of 2, AC, Changed (2)16x25x1 (1) 16x20x4, Performed Cooling Maintenance per checklist, found that the upstairs system is low on charge 1 to 2 lbs of R410A, when system needs refrigerant there is a leak in the refrigerant circuit, system is going on 10 years of age average lifespan is 10 to 15 years and it is recommended to start considering replacing system as leaks get worse over time. With Homeowners permission charged upstairs Lennox system with 2lbs of R410a Psi 1118/289, SH14, SC8, DeltaT 19, systems are running at this time but due to age and condition of upstairs system multiple part failure is possible at anytime.
DCM: Service 1 of 4, system operations check, clear drain lines changed : (8) 16x24x2, (4) 20x20x2, (4) 16x20x2, (2) 16x25x2, (2) 12x20x2, (2) 16x20x1, (1) 10x30x1 Belt Sizes: (2) A39, (1) AX52, (1) A48, (1) A35Check, systems are running this time but Due to age and condition multiple part failure is possible at anytime.
Regardless of the season or the reason you need home or commercial heating and cooling services in Smyrna, GA, Dobbs Heating and Air has the experience and expertise you need. Winter, spring, summer, or fall, all you have to do is call our seasoned HVAC professionals, schedule a FREE on-site assessment of your HVAC repair, replacement, installation, or maintenance need. As your top choice for Smyrna Heating and Air Services, we work harder than any other local HVAC technicians to provide thorough estimates of your best options for all your climate control needs, including but not limited to: