DCM2: Service 2 of 2, Heat Changed (1) 16x25x1 (1) 12x25x1, Performed Heating Maintenance Per Checklist, Systems are running at this time.
Serial: 4TWA4060A4000AC Model: 202428152F Replaced outdoor fan motor and capacitor. Tested system, 5.2A draw, design RLA 6.0. System functions as designed.
Called to move thermostat, had to cut drywall inside closet and run wire inside closet to area requested, talked with Tim while on location and he gave permission to also replace thermostat with T6, installed and tested system is running at this time. Pictures attached.
Call for no cooling upstairs in climate control, first system 2015 Trane found to have a condensation clog full of rust, checked the evaporator coil and found severe rust and corrosion, the condensation pan is broken and Connor be attached to the air handler properly, the aux. pan is in poor condition and rusted through no longer serving its purpose letting water leak out, system was also low on charge added 3lbs of R410A due to the condition and amount of repairs it is recommended to consider replacing system (Pictures Attached). Found that the Second System 2020 Trane has a bad condenser fan motor, the start component was good windings was open will need to send estimate for repair.
DCM1: Service 1 of 2, AC, Checked (1) Aprilaire 413, it was good, Performed Cooling Maintenance Per Checklist System is running at this time.
Heat maintenance on 2-system in Lawrenceville