Khalil rectifies an issue that was caused from the install crew with no issues! Would always recommend Dobbs!
Jonathan was very professional and detailed in his work. He made every effort to make sure that our units were ready for winter.
The guys that come to the house are always respectful and courtesy. They always do a good job and I never feel like something needs to be "fixed" all the time. When my units are in good shape the guys tell me and when there is a problem they find the most reasonable fix for them.
All personnel at facility have always been outstanding. Phone people to techs are all great.
DCM1 service 1 of 2 heat completed changed (2) 14x20x1 filters, tested system operation’s, refrigerant pressure drastically decrease in heating mode, switched over to cooling mode and pressures are proper for outdoor conditions, this indicates the piston is restricted in heating mode. Piston should be replaced in Order to prevent harm to compressor. Will need to call trane and get a price for size 63 piston and send over to landlord.
DCM3 :Service 2 of 2, Heat Checked (2) 16x25x4 Changed (1) 16x20x1, Performed Heating Maintenance Per Checklist, Systems are running at this time.
No heat call unit #22, on arrival thermostat was calling, checked for control voltage and was getting 26v coming out of transformer, system is a Heat Strips only heat system and the smoke detector had Tripp when the heat strips energized, unwired smoke detector and let the system run for a little while to burn off any dust and then wired back in and checked operation system is running at this time.
Returned to replace rollout switch, found on previous visit it was broken and not making contact and stopping the control voltage at that point, replaced and checked operation system is running at this time.
Two system furnace inspection. The upstairs furnace is over 23 years old as well as outdoor condenser. The evaporator coil for upstairs was replaced in 2007 but that’s it. The downstairs system is over 23 years old and has a bad tool out switch. The system is cycling on and off due to vibration of the unit. Replaced both 16x25x1 filters. Upstairs system is working at this time but highly recommend replacing systems.
Inspected current HVAC system and quoted a full system replacement.
Call for insulation coming out of the supply vents, checked all registers inside home and found insulation or debris in all of them, went into crawl space and could hear rodents running throughout the ducting system, will need a reduction on the system.
DCM1 :Service 1 of 2; Heat Changed (1) 16x25x4, Performed Heating Maintenance Per Checklist, system is running at this time
Arrived to System #5 and System #6 drain lines clogged. System share a communal drain. Drainage system had multiple clogs in both the communal lines and individual lines. Cleared all connecting drains. Checked water safeties, function as designed Water had escaped pan on System #6, auxiliary pan drain stub was loose. Tightened to ensure proper seal and to prevent drain pan leakage
DCM3: Service 1 of 2 ; AC completed, (1) 20x20x4-check, (1) 20x25x4-check, (1) Aprilaire 501. Tested systems operations everything is operating properly at this time attached is AC maintenance checklist
When your home or business is in need of HVAC service, you need experts that you can rely on for top-level service, any time and every time you need it. Dobbs Heating and Air’s trained, certified professionals understand the urgency and importance of having a properly working heating and air system. Because you work hard to keep your home and your business operating at optimum levels, you deserve more than just an average tech coming to your front door claiming to be a reliable HVAC service provider. When you choose Dobbs HVAC for your Kennesaw Heating and Air Repair, Replacement, or Installation Needs, you’re getting anything but average service. You get 5-star service for every job, no matter the size, scope, time of day, time of night, or season in which you need HVAC repair, replacement, maintenance, troubleshooting, or installation.
Dobbs Heating and Air has put well over 10+ years into building their business and reputation as a premier local HVAC company. Every Dobbs representative is certified, qualified, and ready to do their best work for your Heating and Air Repair needs in Kennesaw, Marietta, the Greater Atlanta area, Northwest Georgia, or anywhere inside our scope of service areas. Our HVAC company is licensed, insured, bonded, certified, and qualified for any residential HVAC or commercial HVAC needs you have. When you need the best Heating and Air Conditioning service around, Dobbs Heating and Air can provide you with any of the following services, and much more:
You won’t have to worry about quality, experience, and professionalism with Dobbs Heating and Air. We always make sure we bring our best to all of our clients in Kennesaw, Marietta, Greater Atlanta, Northwest Georgia, and beyond. If you need scheduled HVAC Repair or emergency Kennesaw Heating and Air Repair, Dobbs has got your back! The residents of Kennesaw know quality when they see it. That’s how Dobbs Heating and Air has been able to make a name for themselves around Kennesaw and Metro Atlanta. They show up, and get it right the first time. Call us today for premium Kennesaw Heating and Air Repair.
The residents and business owners of Kennesaw, GA love Dobbs Heating and Air’s award-winning HVAC services. After being in the game for over 10 years, Dobbs Heating and Air has been able to establish themselves as experts in the air conditioning installation, repair, and replacement industry. If you’re ever wondering who to choose to install, repair, or replace your heating, ventilation, and air conditioning system, choose Dobbs Heating and Air. Our process is simple and thorough. We listen to your problems, analyze the best strategy for fixing your problems, and then offer the best solutions we can to help solve your HVAC Repair needs. Give us a call today to see how we can help with any of your heating and air conditioning needs!