Really nice tech
Khalil was super nice and he waited for me when I had customer in the office Great Worker !!!
System #2-5 and #8-16 need 1-2lbs of 410. System is slightly low on refrigerant. Saturation temp on both the low and high side are below expected temperatures. Outdoor temp of 57* should result in a saturated temp of 42-37*. Actual temp was 29*. All above systems were identical with regards to temp charge. Most likely reason being a seasonal maintenance plan where the charge was checked using a manifold with long hoses. After enough pressure checks / maintenance checks refrigerant has been slowly removed inside the technicians hoses. Systems have been in place since 2017. System #6- needs 4lbs of 410. System is low on refrigerant. Saturation temp on both the low and high side are well below expected temperatures. Outdoor temp of 57* should result in a saturated temp of 42-37*. Actual temp was 15*
Checked over dust coming out of vents, ducts could need a cleaning, need to to scheduled a comfort specialist out to give quote on cleaning
Air Handler #2 condensate pump needs to be lowered for better fall.
Checked location unit systems.. 15 total systems Split heat pumps Thermostats located actually in the return duct work Old unit left on the roof Unit supports screwed to the roof J joints 11 units on building 4 units on the other
Delivery (6) 10x6 High Velocity registers. Homeowner was rushed for time and elected to install the registers. Confirmed that homeowner was not experiencing any airflow issues since installation. None reported but stated system hasn’t ran that much due to current Georgia weather.
Removed old equipment and all duct work. Installed new rheem 2 stage 3 ton full heat pump system. Installed new supply plenum, new return plenum with 16x20x4 filter, new emergency drain pan, new pan safety switch, new coil safety switch, new drain line, new lineset, new line hide for longest and drain line. Installed all new ductwork, installed new 10” return duct. Replaced supply vents with high velocity vents. Reconnected high voltage and low voltage wires. Tested system operations in heating and cooling, set proper charge. Will need 6 more 10x6 high velocity grilles.
Signed proposal in hvac biz pro -
Heat maintenance on 2-systems in Conyers
Heat maintenance on 5-system in Conyers