Great customer service
Quoted new high efficiency heat pump system
Upon arrival no heat blower motor was not operating, capacitor was reading 0MFD and is a 10MFD. replaced capacitor with homeowners approval, fan started up as intended, system is operating properly at this time, system is 20 years old homeowner would like quoted for replacement confirmed Tuesday the 7th in the 4-5 for comfort specialist.
DCM1 service 2 of 2 heat completed changed (1) 16x25x4 filter, tested operation everything is operating properly at this time attached is Heat maintenance checklist.
DCM1 :Service 1 of 2 ;AC, Changed (1) 20x20x1, Performed Heating Maintenance Per Checklist, System is running at this time but due to age and condition multiple part failure is possible at anytime. Due to ages and condition it is recommended to start considering to replace and upgrading system for better performance, reliability, efficiency, and peace of mind.
DCM2 :Service 2 of 2, Checked (1) 20x25x5, Changed (1) 16x20x1,, Performed Heating Maintenance Per Checklist systems are running at this time.
No a/c upstairs in sons bedroom found wire had come loose from damper and it was not opening and closing properly fixed and checked operation of all dampers they are opening and closing properly at this time.
Call for communication error, their son Tried to connect to thermostat and it quit communicating, turned everything off for 5 mins and turned back on everything connected and running at this time
DCM1 :Service 1 of 2 ;Heat Changed 12x25x1 filter, Performed Heating Maintenance per checklist system is running at this time.
DCM1 service 2 of 2 AC completed changed (1) 20x20x1 filter, tested system operations everything is operating properly at this time attached is AC maintenance checklist.
Returned to replace bad Thermal Expansion Valve that was getting stuck closed, pumped system down, removed bad Thermal Expansion Valve soldered in new Valve, pressure tested to 300 psi held for 15 mins, soap bubbled Valve and my solder joints found no leaks, ran vacuum below 500 microns and released refrigerant back into system checked operation Psi 138/343, SH15, SC5, DeltaT 18 system is running at this time.