Khalil did an outstanding job ensuring the problem was clear, then explaining the solution. Thank you.
Everyone on staff at Dobbs is pleasant and patient answering your questions. Fast service.
DCM2: Service 2 of 2 Heat, Checked 2- 16x25x4, Homeowner buys filters, Humidifier Pad 35 large needs to be replaced will have to return to replace operation was already checked, Performed Heating Maintenance Per Checklist, System is running at this time.
DCM1 Service 2 of 2 - Heat Changed (1) F16201, Performed Heating Maintenance Per Checklist system is running at this time.
DCM2 service 1 of 2 heat completed changed (2) 16x25x4 filter, tested system operation’s everything is operating properly at this time attached is Heat maintenance checklist.
Quoted new gas furnace and air conditioner
Call for no heat, found on prior first when energized the inducer was out of balance found that it is completely rusted out, also found that the Heat Exchanger has a Crack in Cell number 2 found through the high limit, crack is just past the fold, returned to replace failed inducer motor and comprised heat exchanger , installed new heat exchanger and inducer motor checked operation and gas pressure 3.7 in W.C, Heat rise 47 all within spec system is running at this time.
DCM2 service 1 of 2 Heat completed changed (2) 14x25x1 filters, tested system operation’s everything is operating properly at this time attached is Heat maintenance checklist.
Arrived to buzzing in bedroom return. Homeowner has a filter at return plenum and has installed a second filter in a hallway return. The result was greatly increased airflow being moved through bedroom return due to hallway return restriction. Removed unnecessary filter from hallway and harmonic vibration in bedroom return disappeared due to reduced airflow.
Upon arrival loosing a leg of voltage at furnace. Losing a leg of voltage at light switch to furnace. Getting 120V off of breaker. Found splice at ceiling that was a loose connection causing problem. Tightened everything is working
DCM1 :Service 1 of 2, Heat completed (1) Spaceguard 2400. Tested systems operations everything is operating properly at this time attached is Heat maintenance checklist.
Call for no heat, when energized the inducer was out of balance found that it is completely rusted out, also found that the Heat Exchanger has a Crack in Cell number 2 found through the high limit, crack is just past the fold, system is out of labor warranty checked the humidity in crawl space since inducer was so rusted and found that it was %75 and still climbing, it is recommended to consider a whole home dehumidifier to help this issue and help prevent future issues with system and duct work.
Are you having issues with your air conditioning system, and need Powder Springs Heating and Air Repair? You need to call a pro to fix it! Call Dobbs Heating and Air for excellent service on your home and business. Our certified technicians have the knowledge, talent, and equipment to install a new HVAC or repair it completely! If your Heating and Air System can be saved, Dobbs Heating and Air can do it! Dobbs is delighted and proud to serve you with:
Whatever your HVAC needs, Dobbs Heating and Air can handle it. We’re happy to serve the residents and business owners of Powder Springs. You can rely on the Dobbs difference for excellent service done with integrity, honesty, and skilled knowledge. Call us today to get your HVAC unit up and running ASAP!
The weather can be flaky in Powder Springs, but your HVAC system doesn’t have to be! Our Dobbs Heating and Air team is committed to helping you solve your biggest HVAC problems. Through our diligence, we make sure your system is working the way you deserve. Whether you need your heating unit to keep you nice and cozy in the winter,or your air conditioning to keep you chill in the summer, we’re here for you during every season! Give us a call, and we’ll walk you through our HVAC repair, replacement, or installation process.
As the fastest growing air conditioning company in Metro Atlanta, Dobbs Heating and Air is committed to providing award winnings services that every homeowner in Powder Springs will love. Because customer satisfaction is our biggest priority, we’ll never walk away from your HVAC system until you are completely satisfied with our results. When you call us with an HVAC problem, we’ll come to your home, listen to your concerns, analyze all given information for a proper residential or commercial diagnosis, and then offer the best solution for your home or business. Dobbs Heating and Air gets it right the first time around. You can rely on us for a great HVAC system. Call us today!